Sewage Treatment Machine
1.PAC is yellow liquid.
2.PAM is white powder, with 6 per thousand water, and using blender mixing 4-5 hours is ok.
3.Adding drug order: adding PAC first, then PAM, the order can not be reversed.
5.Small batch sewage test: Taking grinding sewage 1 liter first, also adding 1.5-2 ml yellow PAC agent into the measuring cup, and stirring occasionally, then adding 10-15 ml white PAM agent into the measuring cup, after stirring occasionally, and pause, please observed result, if the oil or impurity in sewage is concretionary, and water is getting clear, it means the drug rate is ok; if not, should test again untill the above phenomenon appears. For example, 1 liter sewage needs 2 ml PAC and 10 ml PAM, so 100 liter sewage needs 200 ml PAC and 1000 ml PAM etc..
1.Pumping the sewage into Agitation Tank with Submersible Sewage Pump (about 400 liter), then press the Stirring button, the Agitator Pump will start to stir the mixing sewage.
2.Setting the time of adding PAC or PAM agent, then press start, please pay attention, should add PAC agent first, then PAM agent, after adding the drug, the Agitator Pump should continue to stir about 2-3 minutes.
3.After the sewage is flocculated, precipitating about 15-20 minutes untill the clear water is layered.
4.Open the Water Drain Valve on the Agitation Tank, discharge the clear water into the Clear Water Middle Tank.
5.When the water reaches half or more in the clear water middle tank, please start the filter pump to filter clear water again, at the same time, open the Water Drain Valve of Clear Water Middle Tank. Clear Water Pump need to add a certain amount of water, open the water valve, after adding the water until the clear water pump outflows the clear water, the stop adding the water, and close the water valve.
6.Collect the clear water into the water reservoir or water tank.
7.After the clear water in Agitation Tank drains over, Turn on Multi Disk, at the same time, open the Drain Valve that is on the bottom of Agitation Tank, and drain the sewage sediment into the Multi Disk. When the small water tank of Multi Disk starts to supply the sewage sediment to Multi Disk, please adjust the Drain Valve on the bottom of Agitation Tank, let the water discharge is small, so that the sewage sediment can be drained slowly, because the Multi Disk is running very slowly, the ability of sewage is small, so it needs to drain the mixture of sewage to Multi Disk very slowly.
8.Collected the sludge with Sludge Collect Box.
9.There is 3 pcs of filter cartridge in Filter Pump, after using about 5 time, should take out and clean. And after continuous use about 20 days, should update a new filter cartridge.
Mobile Polishing Machine w/ Automatic unload is firmly packed in an export standard wooden box .